I have been doing as your instructions but get no success. Please see the
my attached project. In this project I have tested with both Unit ID of 0
and 1 but all LC_Numeric_Display fields still display results of 0 (it
should display results greater than 0 as I viewed with other Modbus Tool).
Can you suggest some other hints on this matter ?
I am looking forwards to your assistance.
On Mon, Jan 13, 2014 at 1:37 PM, <qxc(a)gmx.de> wrote:
please find attached a screenshot of the configuration that should fit to
your problem. Regarding the IO base address offset I'm not quite sure, may
be values have to be +-1 since I'm not sure if your PLC/the MOBUS plug-in
starts counting at address 0 or 1
*Gesendet:* Samstag, 11. Januar 2014 um 12:35 Uhr
*Von:* "Mr Lam" <lamtranhn(a)gmail.com>
*Betreff:* Example of Modbus TCP Master
I recently downloaded OpenAPC for Windows x86 (my laptop's OS is Windows 7
Professional, 32bit) and I am getting familiar with Control Room's
functions. I have been trying to get status of digital inputs and value of
holding registers from a Siemens's PLC, which I programmed to work as a
Modbus Server, and display the result to Control Room. But I could not
succeed. I have been using some Modbus tool to check the performance of PLC
and it is still working correctly (inputs and register of PLC give correct
results to Modbus tool).
So I would like to get help from experts of OpenAPC. Particularly I would
like to have a simple example which can read status of Digital Input
Register 1 and content of Holding Regster 40001 to Holding Register 40003.
Thanks in advance
_______________________________________________ openapc mailing list
openapc mailing list
*Mr*. Trần Hồng Lam